The NABIC 500L is designed primarily for use where high tightness is required on the discharge side, having a sealed spring cover to prevent the possibility of back pressure leakage through the top of the valve.
The lift is progressively proportional to flow. All wetted parts are manufactured from dezincification resistance materials. Designed and tested to BS EN ISO 4126 -1.
Medium: Hot water, steam, compressed air, inflammable liquids and inert gasses, Co2 (to 20°C), ethylene glycol, potable water
Size Range: DN15 - DN65
Pressure: 0.4 - 12.5 bar
Temperature: -20 to 195°C
Connection: Screwed inlet & outlet
Screwed female inlet and outlet connections. outlet connection is one size larger than inlet connection. Threaded connections are Rp parallel to BS EN 10226-1. NPT connections are available upon request.
All valves are shell and seat tested (to confirm set pressure) before leaving the factory and all valves are supplied pre-set with a tamper proof seal. Pressure Test Certificate and Letters of Conformity available on request.
|Ref No||Name of Part||Material|
|1||Leak Proof Dome||Bronze, BS EN 1982 CC491K|
|2||Locknut||Brass, BS EN 12164 CW609N|
|3||Dome 'O' Ring||Viton|
|4||Spring||Chrome Vandium Alloy Steel, BS 2803 735 A50 HS (Stainless Steel, BS 2056 302S26 Opt)|
|6||Spring Cover||Bronze, BS EN 1982 CC491K|
|7||Piston||Brass, BS EN 12164 CW609N|
|9||Seat Seal Holder||Bronze, BS EN 1982 CC491K / Brass BS EN 12164 CW602N (DZR)|
|10||Seat Seal||PTFE (Viton Opt)|
|11||Starlock Washer||Stainless Steel|
|12||Body||Bronze, BS EN 1982 CC491K|
|13||Adjusting Screw||Brass, BS EN 12164 CW609N|
|14||Spring Plate||Brass, BS EN 12164 CW609N|
|15||Spindle||Brass, BS EN 12164 CW721R|
|16||Seat Seal Retaining Plate||Bronze, BS EN 1982 CC491K / Brass BS EN 12164 CW602N (DZR)|
Dimensions & Weights
|32||1 1/4"||1 1/2"||54||36||201||2.50|
You must select a value for all options provided.
We had an existing NABIC Fig. 500 safety valve installed in our steam boiler factory which needed replacing. The valve had started to leak due to its old age.
I had no hesitation in purchasing another as it’s been a great product. I was very happy with the service of the website, as well as the prices. The fact the valves come with the necessary certifications is also great.
Wayne Barnes- Engineering Co-ordinator, Newlywed Foods