Supporting the nation's essential services - Read our COVID-19 statement
The NABIC Fig 500 is designed primarily for use on unvented hot water heating systems, where a high capacity, emergency steam relief capability is required.
All wetted parts are manufactured from dezincification resistance materials. Designed and tested to BS EN ISO 4126 -1.
Medium: Hot water, steam, compressed air and inert gasses, Co2 (to 20°C), ethylene glycol, potable water
Size Range: DN15 - DN65
Pressure: 0.4 - 12.5 bar
Temperature: -20 to 195°C
Connection: Screwed inlet & outlet
Screwed female inlet and outlet connections. outlet connection is one size larger than inlet connection. Threaded connections are Rp parallel to BS EN 10226-1. NPT connections are available upon request.
All valves are shell and seat tested (to confirm set pressure) before leaving the factory and all valves are supplied pre-set with a tamper proof seal. Pressure Test Certificate and Letters of Conformity available on request.
|Ref No||Name of Part||Material|
|1||Thrust Washer||Brass, BS EN 12164 CW609N|
|3||Test Lever||Brass, BS EN 1982 CC754S|
|4||Spring||Chrome Vandium Alloy Steel, BS 2803 735 A50 HS (Stainless Steel, BS 2056 302S26 Opt)|
|6||Spring Cover||Bronze, BS EN 1982 CC491K|
|7||Piston||Brass, BS EN 12164 CW609N|
|9||Seat Seal Holder||Bronze, BS EN 1982 CC491K / Brass BS EN 12164 CW602N (DZR)|
|10||Seat Seal||PTFE (Viton Opt)|
|11||Starlock Washer||Stainless Steel|
|12||Body||Bronze, BS EN 1982 CC491K|
|14||Lead Seal (Not shown)||Lead|
|15||Adjusting Screw||Brass, BS EN 12164 CW609N|
|16||Spring Plate||Brass, BS EN 12164 CW609N|
|17||Spindle||Brass, BS EN 12164 CW721R|
|18||Seat Seal Retaining Plate||Bronze, BS EN 1982 CC491K / Brass BS EN 12164 CW602N (DZR)|
Dimensions & Weights
|32||1 1/4"||1 1/2"||54||36||201||2.35|
You must select a value for all options provided.
The reason I went to NABIC was because we have to meet certain water regulations. After a chat with Northumbrian Water, they suggested looking into NABIC products as they are WRAS approved and suitable to use on all potable water applications.
I went direct and bought 4 pipe interrupters with next day delivery, which have been installed in our on-site laboratory. My user experience was great and I liked the fact that site has all the necessary specifications and prices easily to hand.
Peter Bauckham - Managing Director, Argos Inspection